Vulcan Street Sewage Pumping Station (SPS)
CLIENT: Northumbrian Water Group
DATE: March 2021
PROJECT: Vulcan Street
SCOPE OF WORK: The original enquiry was a request for Retroflo to attempt to stop the flow from entering the wet well to enable an inspection of the riser pipes. First attempts failed because the river tees was entering the station through the overflow at high tide, making it impossible to reduce water levels with temporary pumps! Our Client instructed us to employ divers to enter the river tees to inspect the overflow flap valve, which was found laid in the river with failed hinge lugs. Northumbrian Water Group then instructed us to use the divers to install an inflatable stopper to the wet well inlet. This allowed us to pump the wet well down and over-pump the station from the combined sewer overflow. With the wet well successfully isolated from the system we were able to remove the riser pipes which were completely corroded and had snapped. New pipework was procured and on site within four days. We also installed a Penstock on the pumping station inlet c/w with spindle, so in future if NWG needs to isolate the well they can simply close the penstock.
On closer inspection the pump pedestals were found to be corroded beyond use and were no longer fixed to the base of the wet well. After a review of the situation NWG decided the best way forward was to install new pumps and pedestals so our team removed the original, unusable ones in preparation. We then installed temporary electric submersible pumps to continue to over-pump the station while awaiting delivery of new pumps.
When one of the station isolation valves failed during overpumping, NWG also decided to install new isolation valves and NRVs and also take the opportunity to install a permanent over-pumping connection on the rising main for future use.
Retroflo were instructed by NWG to engage the diving company to refit the existing overflow flap valve using a crane on the river banks and to fabricate new hinges to do so. This activity was carried out very successfully and the flap valve is now operable 4 years after it failed .
With the flap valve operable, Retroflo were able to drain the rising main and install the new pedestals, riser pipes, valves and pumps and complete the refurbishment works to make the Pumping Station operate as it should for the first time in 4 years.
COMMENTS FROM OUR CLIENT: 'A very proactive approach from Retroflo on Vulcan Street Sewage Pumping Station (SPS). This scheme has evolved greatly from the initial scope to replace the risers, we have now replaced the flap valve on the river, replaced the stools, pumps, risers, NRV’s and isolation valves due to issues discovered once we got into the SPS. This has been managed excellently by Retroflo and the communication, with all stakeholders, throughout has been first class. A very good job, thank you!'
UK Industrial Tapes Electrical Installation
CLIENT: Uk Industrial Tapes
DATE: December 2017
PROJECT: Supply intake alterations, new sub main cables and distribution boards, wiring to new extension, extension to fire alarm and emergency lighting.
SCOPE OF WORK: Initial liasing with the supply and meter operators to facilitate an upgrade to the supply within the site. Project management of the civils trench works and Northern Powergrid operatives to upgrade the incoming supply. Installation of 315A main switch and supply cable to the existing switch board .Installation of sub main cable and 16 way TPN DB to the rear of the warehouse in readiness for future works. Upgrading of the earthing system. Installation of sub main cable and 11 way SP DB to the new extension. Electrical installation within new extension.
Longacre Flood Alleviation Pumping Station
CLIENT: Northumbrian Water Group
DATE: December 2015 – Jan 2016
PROJECT: Flood Alleviation Site Situated in Houghton-Le-Spring
SCOPE OF WORK: Works consisted of installing a Flood Alleviation pumping station in Houghton-Le-Spring. Retroflo were contracted to supply, install and commission the Mechanical and Electrical works of the site. This included the supply of the Motor Control Center (MCC), Instrumentation, interconnecting cable and associated junction boxes, containment items and earthing installation. Kiosks to house the MCC and REC equipment were also installed.
Commercial EV Charge Point Installation
CLIENT: Jotron Ltd
DATE: October 2017
PROJECT: Installation of 2no Commercial EV charging pedestal via time clock and contactor.
SCOPE OF WORK:
Project included civil works including trench and internal wall break out for cables, back filling trench works, form shutter and form concrete plinth works. Electrical work included installing SWA cabling to trenches, installing distribution board, time clock, contactor and 2x 16A pedestal units to plinth.